Buy ASTM D R GUIDE FOR FLOOD TESTING HORIZONTAL WATERPROOFING INSTALLATIONS from SAI Global. note that ASTM D “Flood Testing Horizontal Waterproofing Installations” is the ASTM method from which this. Technical Data Sheet draws. ASTM D() – Standard Guide for Flood Testing Horizontal Waterproofing Installations0 item(s) – $ View Basket Welcom.
|Published (Last):||5 September 2013|
|PDF File Size:||5.27 Mb|
|ePub File Size:||16.34 Mb|
|Price:||Free* [*Free Regsitration Required]|
ASTM D – 98 Standard Guide for Flood Testing Horizontal Waterproofing Installations
Testing is performed for a minimum of 24 hours and maximum of 72 hours when rainfall is not forecasted to astmm.
Testing Evaluating how your products and services meet and exceed quality, safety, sustainability and performance standards.
Formally confirming that your products and services meet all trusted external and internal standards. If leakage is detected during the test period, water is immediately drained from the test area.
Assurance Testing Inspection Certification.
A containment assembly is constructed to be nondestructive, non-penetrating of the waterproofing installation and easily removable. Flood testing is considered to be completed if no leaks are identified to have occurred during the test period and the membrane and flashings are intact.
Enabling you to identify and mitigate the intrinsic risk in your operations, supply chains and business processes. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of asm limitations prior to use.
Work Item s atm proposed revisions of this standard. This standard is not intended for use on building roofing systems. Need help or have a question?
Global Reach Intertek is the industry leader with over 42, people in 1, locations in over countries. D Terminology Aatm to Roofing and Waterproofing. Note 2 — Increasing the amount of water forming a hydrostatic head beyond mm 4 in.
Certification Formally confirming that your products and services meet all trusted external and internal standards. Applies for fully adhered or bonded sheet membranes, liquid or fluid applied membranes or loose laid sheet membranes of waterproofing installed on parking garages and plaza deck types over habitable spaces or on elevated structures.
Waterproofing membrane and flashings should be inspected and d55957 repaired. Overflows are provided in the containment assemblies, when needed, at 5 inches above low point on the test surface so as asym to exceed the structural capacity of the substrate. Validating the specifications, value and safety of your raw materials, products and assets. Testing should occur prior to the installation of drainage layer, protection layer, pavers or overburden.
Assurance Enabling you to identify and mitigate the intrinsic risk in your operations, supply chains and business processes.
Critical locations shall be monitored during the duration of the test period. Applicable waterproofing membrane installations that may be tested using this guide are fully adhered or bonded sheet membranes, liquid or fluid applied membranes, or loose laid sheet membranes. Through our network of over 43, people in 1, laboratories and offices in countries, Intertek provides quality and safety solutions to a wide range of industries around the world.
ASTM D – 98() Standard Guide for Flood Testing Horizontal Waterproofing Installations
The effects of equipment, planters, or other movable objects present within the test area asym be considered. Following the completion of the repairs and curing of materials, asrm area is retested under the same conditions as the initial flood test. Ponded water can freeze and become adhered to the waterproofing system resulting in pulling or tearing of the flashings away from the substrate or may break interior corners. Test area is flooded with water to achieve a minimum cover of 1 inch but not exceed a maximum depth of 4 inches at the lowest point.
See also ACI Inspection Validating the specifications, value and safety of your raw materials, products and assets. Auditing Consulting Sourcing Training. Lateral loads will be imposed on curbs or walls used for containment of the water during the test procedures and their effect should be accounted for. Link to Active This link will always route to the current Active version of the standard. If a protection layer is required for flood tested, the recommended practice is that a temporary protection layer be loose laid and removed prior to testing of the waterproofing system.
Water height is maintained so as not to exceed a minimum level of 2 inches below the edge of flashings.
Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard. If the product does not meet the performance criteria, additional remediation may be required to pass.
The effects shall be analyzed by a licensed structural engineer prior to placement of additional loads. Asmt Version s – view previous versions of standard.
Evaluating how your products and services meet and exceed quality, safety, sustainability and performance standards. Containment assemblies are composed of a sacrificial sheet or asmt polyethylene sheet adhered to the surface of the waterproofing membrane using a watertight asfm duct tape.
The values given in parentheses are for information only. Whether your business is local or global, we can ensure your products meet quality, health, environmental, safety, and social accountability standards for virtually any market around the world.